PlanoSpot DALI is configured as a sensor only. It cannot control loads, process events or make any bus configurations (addressing, binding). Configuring the PlanoSpot DALI via the DALI bus therefore requires a commissioning device which supports the functionality of PlanoSpot DALI. Detection area, detection sensitivity and room factor may be optionally configured by means of the SendoPro management remote control.
The PlanoSpot DALI presence detector only sends information for presence and luminosity via the DALI bus (i.e. the PlanoSpot DALI acts as a sensor only). Switching, constant light control, handling of manual inputs etc. is done by a DALI master (application controller, implemented in a “SPS”, a DALI gateway etc.).
The PlanoSpot DALI sends one “Instanz” for the presence information and up to 4 “Instanzen” for the luminosity to the bus. The values of these “Instanzen” can be polled individually. In addition these “Instanzen” may be configured to act only event-driven in order to reduce the bus traffic compared to polling mode.
For questions, please contact our staff at the hotline: +41 (0) 52 355 17 27